Waste Water Treatment Plant
Improving Ammonia due to higher than anticipated levels at a wastewater treatment plant.
Due to higher than anticipated Ammonia levels in the influent at this WWTP, the trickling filter system was not adequately reducing the Nitrogen-Ammonia to acceptable levels due to higher than anticipated organic loadings on the system.
To bring the system into compliance the owners determined a solution and to conduct a two-month pilot testing of the proposed solution. They uncovered several major issues after an in-depth study of data and operational equipment. Some of these were with the equipment and others had to do with the process.
Ammonia from the DC influent to the primary septic tank ranged between 55 mg/L and 85 mg/L depending on the time of year, with the Christmas holiday season being the highest. This was the time of year when additional seasonal staff was hired. It was discovered that the water going into the trickling filter was also void of DO, low in pH, and had Ammonia two to three times higher than the design loadings of 25-30 mg/L. Flows ranged from 76,000 to 135,000 litre per day [L/D]. Further, there was insufficient alkalinity to support the metabolic reductions of Ammonia by the resident bacteria in the wastewater and on the filter media.
The entire treatment process time was just 2 days!
A plan was developed to provide an above ground supplemental aeration tank. For the pilot testing a 15,000 litre poly tank was placed on-site as an aeration tank along with a two-inch Venturi Aerator unit with a small centrifugal pump. The Venturi -Aerator unit is designed to add dissolved oxygen (DO) from an ambient air source.
During the cold winter months the Venturi added DO up to 8.0 to 9.5 mg/L and in the very hot summer months DO ranged from 3.5 to 5.0 mg/L. This difference is due to water temperature and the reduced solubility of oxygen in warm and hot water.
The fact that the tank was a dark colour allowed the hot sun to readily heat the water in the summer. The Venturi Aerator was placed in a slightly submerged discharge (600mm) so the kinetic energy of the discharge would spin and mix the contents of the tank. Liquids were pumped into the top of the tank at 60 litres per minute [L/M] displacing an equal volume of treated effluent out of the bottom of the tank.
The pH was also being raised by some stripping of CO2 by the Venturi Aerator from 6.7-6.9 up to 7.2-7.5. This allowed nitrification to occur in the aeration tank, which has a 4 hour hydraulic retention time before being transferred into treatment trains.
A siphon break was added to the discharge piping from the aeration tank. The siphon break was used to add the required additional alkalinity. A total of 7kg of bicarbonate was added daily and dosing was controlled by a small peristaltic metering pump.
The entire treatment process time was two days from when the wastewater was pumped into the aeration tank until it reached a very large leaching field. Residual Nitrogen-Ammonia in the polished effluent to leachfield is: Nitrate 0.18 mg/L; TKN 2.1 mg/L; NH3 0.01 mg/L; and BOD 27.
The Gorman-Rupp Super T Series self priming centrifugal wastewater/sewage pump has been the world benchmark for this technology since 1963 (over 50 years!). They have been designed for economical, trouble-free operation, with superior solids handling capability and a large inspection cover to access pump internals for service or blockage removal.
The Gorman-Rupp Super T Series self-priming centrifugal wastewater/sewage pump has been the world benchmark for this technology since 1963 (>50 years). They have been designed for economical, trouble-free operation, with superior solids handling capability and a large inspection cover to access pump internals for service or blockage removal.
- Self-Priming pump has the ability to mount high and dry above the wet well (not in it)
- Low cost of ownership
- Greatly reduced OH&S issues – no more working over water/heights/cranes/heavy swinging weights
- Surface-mounted pumps with easy access for monitoring or service
- Advanced safety features including pressure relief valve to protect operators
- Improved maintenance features to greatly reduce maintenance time and costs, with removable rotating assembly
- A variety of materials of construction to handle abrasive and/or corrosive fluids
Our Team is available to answer your pump query within the hour
Hydro’s experts are standing by to help you get the best pump, aerators and genuine spare parts for your specific project.
(02) 9898 1800
Monday – Friday
9am – 5pm
Hydro Innovations is proud to be the sole distributor of Gorman-Rupp pumps in Australia.
Gorman-Rupp is one of the world’s leading manufacturers of self-priming sewage pumps and wastewater pumping equipment, and has been for more than 75 years. They offer a diverse range of high performance, high-quality, reliable pumps and pumping systems required for lasting service in wastewater pumps, sewage pumps, industrial waste, petroleum, fire and OEM markets. Learn more about Gorman-Rupp and our other partners »